|RCCSx Power Factor Reactive Current Controlled Switch|
|Site Map||Home||All Products||Process Control & Automation||Power Factor Technology Overview|
|Represent/distribute this product||Request further information/quote||Power factor controls and correction FAQ (Frequently Asked Questions)||Download PDF leaflet||Buy power factor technology on line|
The RCCSx power factor reactive current controlled switch dynamically compensates low inductive power factor lines by switching capacitors in and out of the single or three-phase line. The RCCSx is a fully protected, digitally-controlled and highly integrated unit. It is very simple to install and adaptable to all power factor capacitor compensation applications. The only other parts required to form a complete power factor correction system are a current transformer and the compensating capacitor(s).
RCCS1 Single power factor reactive current controlled switch
RCCS3 Triple power factor reactive current controlled switch
The RCCSx switches measure the reactive current in a single- or three- phase system and activate one (RCCS1) or three (RCCS3) 8 A solid state switches to connect compensating capacitors in and out of the line. The current is detected with a current transformer (CT) in one of the phase lines and the sampling period is selectable from 4 to 32 seconds.
The RCCSx fast response make them particularly suitable for fast dynamic compensation of frequently started, low-duty or variable loads such as:
The RCCSx are designed for standard European and US, single- and three-phase, 50-60 Hz lines. Characterizing features are as follows:
Each capacitor switch is activated when the detected reactive current is above the respective set value as determined at the activation potentiometer. Switch activation/deactivation happens at every sampling instant as set at the DIP switch.
During normal operation each "Switch ON" LED indicates the on or off condition of the relevant switch. In the event of its power circuit overheating, the switch is deactivated and the "Switch ON" LED flashes until power is removed. Overheating is usually the result of switch bypass relay failure and in such a case the worn relay is easily removed from its socket and replaced.
Our power factor related products are summarized here with sampling/small quantities being available for online purchase here.
|Back to top||Site Map||Process Control & Automation||All Products||Power Factor Technology Overview|